Must be installed by a qualified electrician in accordance with all national and local electrical and construction codes and regulations.
Before installing this product, please visit the product page at www.colorkinetics.com for the latest version of the installation instructions. Due to continuous improvements and innovations, installation instructions may change without notice.
Confirm all components received
Verify the electrical plan and all necessary surge protection requirements.
Use Configuration Calculator to help identify and locate all luminaires, Data Enabler Pro devices, and controllers and to calculate the number of luminaires each circuit can support based on model, line voltage, circuit load, and cable lengths.
Data Control Limits
53.3 m (175 ft) maximum individual length
122 m (400 ft) maximum total length
Record location and serial number of each luminaire for addressing.
Make sure power is OFF
Remove cable (Optional)
Loosen cable compression
Secure connections and covers
For wet or damp locations, seal all points of entry to prevent water infiltration. Use RTV silicone and weatherproof junction boxes.
Apply Locktite 263 threadlocker to set screw before tightening.
Attach safety cable
Ensure that main power supply is off before installing or wiring a luminaire.
Do not attempt to install or use a luminaire until you read and understand the installation instructions and safety labels.
Do not use a luminaire if the lens, housing, or power cables are damaged.
Luminaires have line voltage risk of shock and no user serviceable parts. Do not attempt to open them.
Do not use a luminaire for any voltage for which it is not rated. Do not exceed the specified voltage and current input for any luminaire.
LIGHT EXPOSURE HAZARD — Do not access or view luminaire beam closer than 7.5 m (25 ft) during operation
Do not hot swap luminaires. Ensure that power to the series is off before connecting or disconnecting individual luminaires.
This device complies with Part 15 of the FCC Rules. Operation is subject to the following two conditions: (1) this device may not cause harmful interference, and (2) this device must accept any interference received, including interference that may cause undesired operation.
This equipment has been tested and found to comply with the limits for a Class A digital device, pursuant to Part 15 of the FCC Rules. These limits are designed to provide reasonable protection against harmful interference when the equipment is operated in a commercial environment. This equipment generates, uses, and can radiate radio frequency energy and, if not installed and used in accordance with the instruction manual, may cause harmful interference to radio communications. Operation of this equipment in a residential area is likely to cause interference in which case the user will be required to correct the interference at his own expense.
This Class A digital apparatus complies with Canadian ICES-003. Cet appareil numérique de la classe A est conforme à la norme NMB-003 du Canada.
The external flexible cable or cord of this luminaire cannot be replaced; if the cord is damaged, the luminaire shall be destroyed. 此灯具的外部软缆或软线不能替换；如果软线损坏，该灯具即应报废